There is only a Hot and a Neutral. 120VAC is one leg. The 60V is probably just a phantom reading. In short, you have a bad connection, broken wire somewhere, probably on the neutral. You might try measuring the hot to the neutral on another outlet. If your not comfortable around electricity you may want to call an electrician on this one.
2015 38GK, Titan Brakes, H 114 Tires, IS
2015 Denali Dually